891 El Placer Rd Palm Springs CA 92264
891 El Placer Rd Palm Springs CA 92264 – This is a Single-Family Home located at 891 El Placer Road, Palm Springs CA. 891 El Placer Rd has 3 beds, 1
½ bath, and approximately 1,334 square feet. The property has a lot size of 6,098 sq. ft and was built in 1977. The average list price for similar homes for sale is $295,355 and the average sales price for similar recently sold homes is $275,100. 891 El Placer Rd is in the 92264 ZIP code in Palm Springs, CA. The average list price for ZIP code 92264 is $562,448. – Description provided by Trulia
Sampling of Signature Home Inspection Observations during this Palm Springs Home Inspection
Repair/Replace, Evaluate , Conducive conditions – Corrosion was found in one or more areas on the water heater, and water stains were found below. The water heater may be failing. A qualified plumbing contractor should evaluate and replace water heater if necessary.
Repair/Replace, Evaluate – The water supply pressure is greater than 80 psi. Pressures above 80 psi may void warranties for some appliances such as water heaters or washing machines. Flexible supply lines to washing machines are more likely to burst with higher pressures. Typically the pressure cannot be regulated at the water meter. Recommend having a qualified plumber evaluate and make modifications to reduce the pressure below 80 psi. Installing a pressure reducing valve on the main service pipe is a common solution to this problem. If one exists, then it should be adjusted for lower pressures.
Major Defect, Evaluate , Conducive conditions – The roof surface material appears to be near the end of its service life and will likely need replacing in the near future, even with repairs. The client(s) should budget for a replacement roof surface, and may want to have a qualified roofing contractor evaluate and attempt to issue a “5 year roof certificate”.
Safety, Repair/Replace, Evaluate – Neutral wires are doubled or bundled together on the neutral bus bar. This is unsafe due to the need to turn off multiple circuit breakers to work on any of the circuits using these wires. A qualified electrician should evaluate and repair as necessary.
Signature Home Inspection is a Certified Home Inspection service located in California serving Orange County, San Diego County, Los Angeles County, Riverside County, Santa Clara County, San Mateo County, San Francisco County, Contra Costa County, and San Bernardino County California.
Leave a ReplyWant to join the discussion?
Feel free to contribute!